Installation and commissioning of Addressable detection linking to coincidence panels activating Gas extinguishing, the project was made difficult due to there being only one addressable panel controlling 5 extinguishing areas.
We installed over 150 detectors, and 48 Gas extinguisher bottles. The system was set up so that any smoke detector would cause a first stage alarm and any 2 detectors cause a second stage alarm and initiating a gas release once the countdown timers reach 0 from 30 seconds. There are also signals sent to the House fire alarm system and BMS.
To complement the point detection installed we also commissioned a VESDA system to give an early warning of any potential fires. We also had the task of bringing the house system up to date by ensuring the new outbuilding had the correct coverage to protect the site.